The alarm at the control unit has been triggered. What should I do?
Press the alarm button to turn off the buzzer.When the alarm is set off, the system is shut down and stops operating.
Press the alarm button to turn off the buzzer.
When the alarm is set off, the system is shut down and stops operating. There are only two reasons why the alarm might sound:
Failure of the titanium electrodes/OXY system (production of Hydroxyl)
Failure of the copper electrodes/ION system (production of Copper)
A red LED indicates which channel it is. To resolve the problem, you should proceed in the same way, irrespective of the channel:
Lack of salt (low water conductivity)
Electric cables are failing to make proper contact at the electrodes
A green internal cable plug has come adrift
An internal cable has come out of its plugElectrodes are wasted away or degraded